When fire breaks out on an industrial worksite or in a manufacturing facility, the effect—on people, property, and profitability—can be significant. In the US, between 2009 and 2013, fire departments responded to an estimated average of 37,000 industrial or manufacturing fires each year, resulting in
The stakes are high, and the risk is great. It is not surprising, then, that, when decisions are made about equipping worksites with fire extinguishers—the first line of firefighting defense—most organizations insist on quality. Often, decision-makers defer to the UL fire ratings, with the expectation that the higher the rating the better the firefighting capability. For some fires, that is true; however, when it comes to fires in high-risk environments, the opposite can be true.
The National Fire Protection Association (NFPA) recognized this anomaly in its 2007 NFPA 10, Subsection 5.5, which covers specific hazards including pressurized flammable liquids and gasses, 3D fires, and obstacle fires. For these Class B fires, the NFPA 10 technical committee concluded that extinguisher size and flow rates should be the basis of extinguisher selection, not UL fire ratings, because the ratings on higher-flow extinguishers tend to be lower than those on lower-flow units.
Because Section 5.5 calls for selecting extinguishers that may have lower UL fire ratings, it is counterintuitive to many. As a result, a great deal of confusion remains about high-flow fire extinguishers in the marketplace today. How can lower-rated extinguishers possibly be more effective in suppressing certain fires than those with higher UL ratings? Unfortunately, the confusion can put people, property, and profitability at unnecessary risk.
Understanding the High-Risk/Low-UL-Rating Connection
When establishing a fire extinguisher Class B rating, one of the UL 711 considerations is discharge time—the length of time it takes for the dry chemical agent to discharge from the extinguisher. For certain fires, the longer the discharge, the better, and a longer discharge time may offer novice users time to correct any misapplication.
The slow rate of discharge, however, becomes problematic in high-risk environments where there is a greater likelihood of pressure fires and gravity fed/3D and obstacle fires. In these situations, the operator needs an extinguisher that meets or exceeds a minimum of 1-lbm/sec flow rate. In other words, the operator needs a high-flow extinguisher that delivers a lot of chemical—quickly. Yet, because high-flow extinguishers tend to have lower UL ratings (because of UL’s discharge time criteria), they are sometimes dismissed as being less capable when, in fact, they are the optimal choice for these high-risk environments.
The NFPA 10 technical committee, recognizing the inconsistency, established this standard a decade ago; now, new test results validate that standard.
What the New Test Results Show
In the summer of 2017, Johnson Controls conducted a series of tests designed to compare the firefighting effectiveness of various extinguishers in flammable liquid in-depth and pressurized flammable liquid and gas fires. The results confirm the findings of NFPA 10, Subsection 5.5, 10 years earlier.
Under the test conditions, across multiple types of Class B fires in high-risk environments, high-flow cartridge-operated extinguishers provided the best protection even though they may not have the highest UL ratings.
Not All High-Flow Extinguishers are Created Equal
Although the most recent tests continue to show high-flow extinguishers can perform better in high-risk environments with flammable liquids and gases, not all high-flow extinguishers are created equal. It is important to have the right tool for the job; one that will minimize risk to people and property in the event of a fire and that also will deliver the best return on investment.
For example, a cartridge-operated portable extinguisher typically carries a higher initial cost when compared with a stored-pressure model. But, leading cartridge-operated models offer greater lifetime value because their features are designed specifically for the operational and environmental challenges of high-risk industries.
When Uptime is a Priority
High-risk environments require worksite fire extinguishers to be fully functional before any work can commence. So, if an extinguisher has been used, damaged, or accidentally discharged, there can be considerable downtime until the unit is replaced or recharged.
A cartridge-operated portable extinguisher can be recharged on site in a matter of minutes without any special tools, which means the process will typically have little or no effect on uptime. By contrast, stored-pressure extinguishers must be recharged by a trained service technician at a distributor’s shop using special equipment or by bringing a qualified technician and their equipment directly to the site, which can also cause considerable downtime.
When Durability is a Priority
In tough, high-hazard environments, fire extinguishers are put to the test. They may be subject to heavy vibration, hard shocks, harsh weather, or direct sunlight—less-than-optimal conditions. It is not unusual, for example, for gauges on stored-pressure extinguishers to become damaged, for valves to break off, for leaks to occur, or for Mylar nameplates to fade in direct sunlight, making it difficult to know if the model meets current listing standards or should be removed from service. Quality cartridge-operated portable extinguishers, by contrast, leave little to chance. They are designed specifically to endure conditions found in most industrial, high-risk environments, with heavier-gauge steel shells, fewer potential leak paths than stored-pressure models, and the elimination of inherently fragile gauges. Also, as a result of the propellant-cartridge discharge, the agent is fluidized immediately before use, which helps to combat the compaction effects of significant vibration.
When Reliability is a Priority
A fire extinguisher can only be effective if it works when it is needed. Cartridge-operated portables are designed so that all moving parts can be inspected at any time, not just every 6 years, as is the case with stored-pressure models.
By offering easy, any-time accessibility to the mechanics of the extinguisher, cartridge-operated portables give everyone at the worksite the confidence of knowing that, if they reach for an extinguisher, it will perform as expected, because there are no second chances when it comes to fighting fire.
When Ease-of-Use is a Priority
To fight any fire effectively, the person operating the extinguisher must be able to move around easily and safely while holding the extinguisher. This is especially critical in high-risk environments where the operator may not be able to run away from the threat. For that reason, flexibility and ease of use is often a priority for organizations focused on minimizing risk.
Today’s leading cartridge-operated portables take ease of use into consideration, with ergonomically designed features to maximize operator performance. Carrying handles are positioned so the extinguisher hangs at a 45° angle off to the side so it can be easily carried up and down stairs. Nozzles are designed to point at the base of the fire when squeezed for easier and more precise agent delivery. Hoses are longer, giving operators greater flexibility to use the fire extinguisher.
When combined, features such as these make it possible for people to fight fires more effectively, minimize potential damage to property, and, most importantly, minimize risk to themselves and their colleagues.
The Right Tool for the Toughest Jobs
In high-risk environments, cartridge-operated high-flow extinguishers are designed to deliver a number of advantages over traditional stored-pressure models: greater uptime, ease of use, durability, and reliability. Combined, these attributes deliver not only the best firefighting effectiveness when faced with pressure, obstacle, or 3D fires, but they can also deliver a greater lifetime value.
While the selection of a high-flow extinguisher may seem counterintuitive because it may have a lower rating, remember that, in these situations, higher flow rate is more important than UL fire rating. The NFPA recognized this in its 2007 edition of NFPA 10, and recent testing validates that NFPA mandate. As a result, professionals in high-risk industries are urged to look beyond the UL rating and ensure they select extinguishers with the firefighting capability, reliability, and durability necessary to protect people, property, and profitability in the event of a fire.
Find more about Johnson Controls fire suppression here.
Don't miss our latest HSE content, delivered to your inbox twice monthly. Sign up for the HSE Now newsletter. If you are not logged in, you will receive a confirmation email that you will need to click on to confirm you want to receive the newsletter.
3 Oct 2019
- Calgary, Alberta, Canada
Being Human - reserve your place at this one-day course
3 - 4 Oct 2019
- Calgary, Alberta, Canada
For a better understanding of geomechanical factors, attend this course
1 Nov 2019
- Bali, Indonesia
Don't miss out!
9 - 11 Nov 2019
- Abu Dhabi, UAE
The programme combines expert input, case studies, and immersive scenarios from the E&P and other industries to embed your learning and enable you to progress to the next level of your career.
10 Nov 2019
- Abu Dhabi, United Arab Emirates
Safety Leadership focuses on the ‘Human Factors’ (HF) which complement technical training to optimize reliability, safety, compliance, efficiency and risks within a team-based environment.
This course will help you develop a better understanding of factors that could impact your daily economic decisions as well as establish a new set of applicable tools to use in your professional career.
Through this workshop, attendees will go through the different processes involved in strategic planning including the elements of organizational SWOT, business scenario and options development, elaboration of strategic options and communication to stakeholders.
HSE Now is a source for news and technical information affecting the health, safety, security, environment, and social responsibility discipline of the upstream oil and gas industry.
©2003-2019 Society of Petroleum Engineers, All Rights Reserved.